|Place of Origin:||Mainland China|
|Brand Name:||Chengtiantai cable|
|Minimum Order Quantity:||500 M|
|Packaging Details:||Steel wooden Drum|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, T/T|
Fire resistant cable 0.6/1kV single core | cu-conductor, mica tape, XLPE Insulation, LSZH Sheath
These cables are used for electricity supply in low voltage installation system, They are suitable for installation in indoors and outdoors, in cable ducts, under ground, in power and switching stations, local energy distributions, industrial plants, where there is no risk of mechanical damage.
The conductors shall be either of Class 1 or Class 2 of plain or metal-coated annealed copper or of plain aluminium or aluminium alloy, or of Class 5 of plain or metal-coated copper in accordance with IEC 60228.
XLPE material and thickness shall be as per IEC 60502 or BS 5467 rated for 90°C continuous operation.
The inner coverings may be extruded or lapped. For cables with circular cores, except cables with more than five cores, a lapped inner covering shall be permitted only if the interstices between the cores are substantially filled. A suitable binder is permitted before application of an extruded inner covering. The material is compatible with the insulating material,The materials used for inner coverings and fillers shall be suitable for the operating temperature of the cable and compatible with the insulating material.For halogen free cables, the inner covering and fillers shall also be halogen free compound.
Aluminum/galvanized steel/steel wires applied helically over the Inner Covering as per IEC 60502-1, or double aluminum/steel tapes and copper/tinned copper wire can also be manufactured upon request.
Outer sheath shall be of extruded PVC Type ST1/ST2 as per IEC 60502-1, Polyethylene type ST3/ST7, Halogen free compound ST8, Polychloroprene, chlorosulfonated polyethylene or similar polymers, type SE1 are also available on request.
Cables can be supplied with special flame retardant PVC outer sheath to comply with the flame test requirements of IEC 60332-3-22, IEC 60332-3-23 and IEC 60332-3-24, Halogen Free material comply to IEC60754-1/2 and IEC 60684-2.
SINGLE CORE CABLE (UNARMOURED) Physical and Electrical Characteristics:
|Current ratings in air 30℃||Current ratings buried 20℃||maximum DC resistance at 20℃|
|mm²||mm||mm||mm||kg / km||A||A||Ω/km|
|A1 – Thermally insolated wall (Single-core)||A2 – Thermally insolated wall (multi-core)||B1 – Apparent electroduct (Single-core)||B2 – Apparent electroduct (multi-core)|
|B1 – Electroduct in brickwork (Single-core)||B1 – Electroduct in brickwork (multi-core)||C – On the wall||C – On the ceiling|
|C – Non-perforated tray||F – Perforated tray (Single-core)||F – Perforated tray (multi-core)||F –Suspended (Single-core)|
|E – Suspended (multi-core)||B2 – Construction space||B2 – Construction space||B1 – Electroduct (Single-core)|
|B2 – Electroduct (Multi-core)||B2 – Closed raceway embedded in floor (multi-core)||B2 – Closed raceway embedded in floor (multi-core)||B1 – Ventilated raceway embedded in floor|
|C – Embedded in the brickwork||D – Buried in additional mechanical protection|
|CABLE DRUMS||D1=Flange Diameter(mm)||W=Useful Width (mm)||D2=Barrel Diameter(mm)|
RECOMMENDED ORDERING PARAMETERS
For prompt quotation / supplies please make sure your inquiries and your orders are
1 - International or Special Standard. (Alternatively, the precise usage of the cable.)
If this all seems a litle too technical for you, then why not get in touch with us.
We look forward to assisting you in identifying the best products for your specific application and to answer any questions you might have.
Tel:+86 755 6114 5028
For a period commencing on the date shipped the Goods to Buyer and continuing for a period of 12 months thereafter.
|Voltage:||0.6/1kV||Conductor:||Bear Copper Cl.2|
|No. Of Conductor:||Single Core||1st Insulation:||Mica Tape|